<Product Revision="5" xmlns="https://github.com/OpenZWave/open-zwave">
  <!-- 
Qubino: ZMNHDDx Flush Dimmer Z-Wave+
ZMNHDD1 868,4 MHz
ZMNHDD2 921,4 MHz
ZMNHDD3 908,4 MHz
ZMNHDD4 869,0 MHz
ZMNHDD5 916,0 MHz

http://qubino.com/download/990/
-->

	<!-- Configuration -->
  <CommandClass id="112">
    <Value genre="config" index="1" instance="1" label="Input 1 switch type" max="1" min="0" size="1" type="list" value="0">
      <Help/>
      <Item label="Mono-stable(push button)" value="0"/>
      <Item label="Bi-stable" value="1"/>
    </Value>
    <Value genre="config" index="2" instance="1" label="Input 2 switch type" max="1" min="0" size="1" type="list" value="0">
      <Help/>
      <Item label="Mono-stable (push button)" value="0"/>
      <Item label="Bi-stable" value="1"/>
    </Value>
    <Value genre="config" index="3" instance="1" label="Input 2 contact type" max="1" min="0" size="1" type="list" value="0">
      <Help/>
      <Item label="NO (normally open)" value="0"/>
      <Item label="NC (normally close)" value="1"/>
    </Value>
    <Value genre="config" index="4" instance="1" label="Input 3 contact type" max="1" min="0" size="1" type="list" value="0">
      <Help>Default value 0</Help>
      <Item label="NO (normally open)" value="0"/>
      <Item label="NC (normally close)" value="1"/>
    </Value>
    <Value genre="config" index="10" instance="1" label="Activate / deactivate functions ALL ON/ALL OFF" max="255" min="0" size="2" type="list" value="255">
      <Help>Flush dimmer module responds to commands ALL ON / ALL OFF that may be sent by the main controller or by other controller belonging to the system.
			Default value 255.</Help>
      <Item label="ALL ON active, ALL OFF active" value="255"/>
      <Item label="ALL ON is not active ALL OFF is not active" value="0"/>
      <Item label="ALL ON is not active ALL OFF active" value="1"/>
      <Item label="ALL ON active ALL OFF is not active" value="2"/>
    </Value>
    <Value genre="config" index="11" instance="1" label="Automatic turning off output after set time" max="32536" min="0" size="2" type="short" value="0">
      <Help>0 - Auto OFF disabled.
			1 second to 32536 seconds Auto OFF enabled with defined time, step is 1 second.
			Default value 0.</Help>
    </Value>
    <Value genre="config" index="12" instance="1" label="Automatic turning on output after set time" max="32535" min="0" size="2" type="short" value="0">
      <Help>0 - Auto ON disabled.
			1 second to 32535 seconds Auto ON enabled with defined time, step is 1 second.
			Default value 0.</Help>
    </Value>
    <Value genre="config" index="20" instance="1" label="Enable/Disable 3-way switch/additional switch" max="2" min="0" size="1" type="list" value="0">
      <Help>Dimming is done by push button or switch connected to I1 (by default).
				Enabling 3-way switch, dimming can be controlled by push button or switch connected to I1 and I2.
				Default value 0.
			</Help>
      <Item label="single push button (connected to I1)" value="0"/>
      <Item label="3-way switch (connected to I1 and I2)" value="1"/>
      <Item label="Additional switch (connected to I2)" value="2"/>
    </Value>
    <Value genre="config" index="21" instance="1" label="Enable/Disable Double click function" max="1" min="0" size="1" type="list" value="0">
      <Help>If Double click function is enabled, a fast double click on the push button will set dimming power at maximum dimming value.
				Default value 0.</Help>
      <Item label="Disabled" value="0"/>
      <Item label="Enabled" value="1"/>
    </Value>
    <Value genre="config" index="30" instance="1" label="Saving the state of the relay after a power failure" max="1" min="0" size="1" type="list" value="0">
      <Help>Default value 0.</Help>
      <Item label="Flush dimmer module saves its state before power failure (it returns to the last position saved before a power failure)" value="0"/>
      <Item label="Flush dimmer module does not save the state after a power failure, it returns to off position" value="1"/>
    </Value>
    <Value genre="config" index="40" instance="1" label="Power reporting in Watts on power change" max="100" min="0" size="1" type="byte" value="5">
      <Help>Set value from 0 - 100 (0% - 100%).
			0 - Reporting Disabled.
			1 - 100 = 1% - 100% Reporting enabled.
			Power report is send (push) only when actual power in Watts in real time change for more than set percentage comparing to previous actual power in Watts, step is 1%.
			Default value 5.</Help>
    </Value>
    <Value genre="config" index="42" instance="1" label="Power reporting in Watts by time interval" max="32767" min="0" type="short" value="300">
      <Help>Set value means time interval (0 - 32767) in seconds, when power report is send.
			0 - Reporting Disabled.
			1 second to 32767 seconds reporting enabled.
			Power report is send with time interval set by entered value.
			Default value 300 (power report in Watts is send each 300s).</Help>
    </Value>
    <Value genre="config" index="60" instance="1" label="Minimum dimming value" max="98" min="1" type="byte" value="1">
      <Help>1 - 98 = 1% - 98%, step is 1%. Minimum dimming values is set by entered value.
			Default value 1 (Minimum dimming value is 1%).</Help>
    </Value>
    <Value genre="config" index="61" instance="1" label="Maximum dimming value" max="99" min="2" type="byte" value="99">
      <Help>2 - 99 = 2% - 99%, step is 1%. Maximum dimming values is set by entered value.
			Default value 99 (Maximum dimming value is 99%).</Help>
    </Value>
    <Value genre="config" index="65" instance="1" label="Dimming time (soft on/off)" max="255" min="1" type="short" value="100">
      <Help>Set value means time of moving the Dimmer between min. and max. dimming values by short press of push button I1 or controlled through.
			1- 255 = 10mseconds - 2550mseconds (2,55s), step is 10mseconds.
			Default value 100 (Dimming time between min. and max. dimming values is 1s).</Help>
    </Value>
    <Value genre="config" index="66" instance="1" label="Dimming time when key pressed" max="255" min="1" type="short" value="3">
      <Help>Time of moving the Dimmer between min. and max dimming values by continues hold of push button I1.
			1- 255 = 1 second - 255 seconds.
			Default value 3 (Dimming time between min. and max. dimming values is 3s).</Help>
    </Value>
    <Value genre="config" index="67" instance="1" label="Ignore start level" max="1" min="0" size="1" type="list" value="0">
      <Help>This parameter is used with association group 4.
				A receiving device SHOULD respect the start level if the Ignore Start Level bit is 0.
				A receiving device MUST ignore the start level if the Ignore Start Level bit is 1.
				Default value 0.</Help>
      <Item label="respect start level" value="0"/>
      <Item label="ignore start level" value="1"/>
    </Value>
    <Value genre="config" index="68" instance="1" label="Dimming duration" max="1" min="0" size="1" type="list" value="0">
      <Help>This parameter is used with association group 3.
				The Duration field MUST specify the time that the transition should take from the current value to the new target value.
				A supporting device SHOULD respect the specified Duration value.
				Default value 0.</Help>
      <Item label="Respect start level" value="0"/>
      <Item label="Ignore start level" value="1"/>
    </Value>
    <Value genre="config" index="100" instance="1" label="Enable / Disable Endpoints I2 or select Notification Type and Event" max="9" min="0" size="1" type="list" value="1">
      <Help>Enabling I2 means that Endpoint (I2) will be present on UI.
			Disabling it will result in hiding the endpoint according to the parameter set value.
			Additionally, a Notification Type and Event can be selected for the endpoint.
			Endpoint device type selection: notification sensor (1 - 6) sensor binary (9).
			NOTE: After parameter change, module has to be re included into the network in order setting to take effect!
			Default value 1.</Help>
      <Item label="Home Security; Motion Detection, unknown location." value="1"/>
      <Item label="Carbon Monoxide; Carbon Monoxide detected, unknown location." value="2"/>
      <Item label="Carbon Dioxide; Carbon Dioxide detected, unknown location." value="3"/>
      <Item label="Water Alarm; Water Leak detected, unknown location." value="4"/>
      <Item label="Heat Alarm; Overheat detected, unknown location" value="5"/>
      <Item label="Smoke Alarm; Smoke detected, unknown location" value="6"/>
      <Item label="Endpoint, I2 disabled" value="0"/>
      <Item label="Sensor binary" value="9"/>
    </Value>
    <Value genre="config" index="101" instance="1" label="Enable / Disable Endpoints I3 or select Notification Type and Event" max="9" min="0" size="1" type="list" value="1">
      <Help>Enabling I3 means that Endpoint (I3) will be present on UI.
			Disabling it will result in hiding the endpoint according to the parameter set value.
			Additionally, a Notification Type and Event can be selected for the endpoint.
			Endpoint device type selection: notification sensor (1 - 6) sensor binary (9).
			NOTE: After parameter change, module has to be re included into the network in order setting to take effect!
			Default value 1.</Help>
      <Item label="Home Security; Motion Detection, unknown location." value="1"/>
      <Item label="Carbon Monoxide; Carbon Monoxide detected, unknown location." value="2"/>
      <Item label="Carbon Dioxide; Carbon Dioxide detected, unknown location." value="3"/>
      <Item label="Water Alarm; Water Leak detected, unknown location." value="4"/>
      <Item label="Heat Alarm; Overheat detected, unknown location" value="5"/>
      <Item label="Smoke Alarm; Smoke detected, unknown location" value="6"/>
      <Item label="Endpoint, I3 disabled" value="0"/>
      <Item label="Sensor binary" value="9"/>
    </Value>
    <Value genre="config" index="110" instance="1" label="Temperature sensor offset settings" max="32536" min="1" type="short" value="32536">
      <Help>Set value is added or subtracted to actual measured value by sensor.
			32536 : offset is 0.0C.
			From 1 to 100 : value from 0.1 C to 10.0 C is added to actual measured temperature.
			From 1001 to 1100 : value from -0.1 C to -10.0 C is subtracted to actual measured temperature.
			Default value 32536.
			</Help>
    </Value>
    <Value genre="config" index="120" instance="1" label="Digital temperature sensor reporting" max="127" min="0" type="byte" value="5">
      <Help>If digital temperature sensor is connected, module reports measured temperature on temperature change defined by this parameter.
			0 : Reporting disabled.
			1- 127 = 0,1C - 12,7C, step is 0,1C.
			Default value 5 = 0,5C change.
			</Help>
    </Value>
  </CommandClass>
  <!-- Association Groups -->
  <CommandClass id="133">
    <Associations num_groups="11">
      <Group index="1" label="Lifeline" max_associations="1"/>
      <Group index="2" label="Basic on/off input I1" max_associations="16"/>
      <Group index="3" label="Multilevel set Flush dimmer" max_associations="16"/>
      <Group index="4" label="Start level change/stop level change input I1" max_associations="16"/>
      <Group index="5" label="Basic on/off input I2" max_associations="16"/>
      <Group index="6" label="Notification report input I2" max_associations="16"/>
      <Group index="7" label="Binary sensor input I2" max_associations="16"/>
      <Group index="8" label="Basic on/off input I3" max_associations="16"/>
      <Group index="9" label="Notification report input I3" max_associations="16"/>
      <Group index="10" label="Binary sensor input I3" max_associations="16"/>
      <Group index="11" label="Multilevel sensor report temp sensor" max_associations="16"/>
    </Associations>
  </CommandClass>
  <!-- Remove COMMAND_CLASS_BASIC -->
  <CommandClass action="remove" id="32"/>
  <!-- Map endpoints to instances -->
  <CommandClass id="96">
    <Compatibility>
      <MapRootToEndpoint>true</MapRootToEndpoint>
    </Compatibility>
  </CommandClass>
</Product>
